Trane VX95 Short Cycle Error Fixed by Cleaning Flame Rod
Trane VX95 Gas Furnace
Trane VX95 Flame Sensor Rod Location
Trane VX95 Gas Furnace Error Code List
The suggested solution was to remove and clean the flame rod and reinstall it.
After turning off the AC power at the circuit breaker panel and turning off the
gas valve, I removed the flame sensor rod and sure enough, it had a slight coating
of residue on it. A few seconds of scrubbing it with a piece of ScotchBrite pad
gave it a nice shiny look. It was put back in place, power and gas turned back on,
and the furnace fired and functioned normally again.
Trane VX95 Flame Sensor Rod Before and After Cleaning
"Why does the gas furnace short cycle?" YouTube video, by
Hopefully, by posting this information other people will be able to remedy similar
BTW, when I first went to turn off the local switch for the furnace, it did not
work; the furnace kept running. Jiggling the lever made it work, but I replaced
it out of an abundance of caution. This house was built in 1956, and the Slater
4200-SP appears to be the original. "Lifetime Switches" is molded into the bottom
of the case, so I guess the 'lifetime' definition is up for interpretation
(kind of like what the meaning of 'is' is). I was
hoping it would be a mercury switch as was common with the early 'silent' type,
since it initially did not make the familiar snapping sound when changing positions.
It turns out the lack of a snap was a symptom of the switch not working at all.
After exercising it a few times, the snap returned, but I will not bother re-installing
News Flash: I needed to do the same type
flame sensor repair to my A.O. Smith GCV 40 100 gas hot water heater
RF Cafe began life in 1996 as "RF Tools" in an AOL screen name web space totaling
2 MB. Its primary purpose was to provide me with ready access to commonly needed
formulas and reference material while performing my work as an RF system and circuit
design engineer. The World Wide Web (Internet) was largely an unknown entity at
the time and bandwidth was a scarce commodity. Dial-up modems blazed along at 14.4 kbps
while tying up your telephone line, and a nice lady's voice announced "You've Got
Mail" when a new message arrived...
Copyright 1996 - 2026
All trademarks, copyrights, patents, and other rights of ownership to images
and text used on the RF Cafe website are hereby acknowledged.