Qualified and competent electrical workers are required to perform a variety of tasks
with and around higher voltage electricity, electrical equipment, and apparatus. The
nature of such work necessitates an understanding of applicable safety policies and rules.
Many electrical hazards and work practices are the same regardless of the voltage
involved. However, due to the nature of high voltage work, there are many hazards and
work practices that are specifically related to high voltage. Refer to chapter 2 of this
document for more details.
This section provides safety guidelines and requirements for carrying out assigned
job tasks. It is essential that each employee exercise sound judgment to perform assigned
tasks safely. Safety is the responsibility of each employee.
The greatest responsibility for a worker's safety lies directly with the worker. This
means that all workers are responsible for performing their work in a manner that does
not endanger themselves, their co-workers, or others in the area and for complying with
safety rules and requirements. Workers should not rely solely on the care exercised by
another for their protection. Workers are encouraged to contribute to the safety program
and bring to the attention of their supervisors or safety representative any condition
they believe is unsafe.
1. The worker should examine the work area for existing hazards and proceed in a safe
2. When seen in a dangerous situation, fellow workers should be warned in such a manner
as to avoid confusing, startling, or suddenly alarming them.
3. Before climbing poles, ladders, or other such structures or before working on scaffolds,
workers shall make a careful inspection to determine whether the structures are safe
and are properly supported. Workers should not carry anything in their hands while ascending
or descending ladders. Small objects or tools may be carried in pockets or pouches. Larger
objects, however, should be raised or lowered by use of hand lines or ropes and blocks.
Others working nearby or below should remain out of line of the work area in case anything
should accidentally be dropped.
4. It is the responsibility of each worker to attend safety meetings. Workers should
also make a practice of learning safety information made available to them that will
help them perform their work more safely.
5. The worker shall report to the supervisor any personal injury as defined by the
facility as soon as possible.
6. The worker should exercise care and good judgment when lifting heavy material,
obtaining help if the object is too heavy or awkward for one person to handle.
Supervisors are responsible for knowing and implementing applicable safety policies
and directives and taking action as required to provide for the safety of the personnel
and operations they supervise. This includes; taking positive action to determine and
reduce, as necessary, the hazards associated with their operations; instructing employees
in safe work methods and associated safety requirements; allowing only those employees
that are qualified for the work to perform the work; and ensuring that employees perform
their work safely.
Supervisors shall be responsible for the safety of all employees under their supervision.
They shall enforce the rules that apply to the hazards involved.
Supervisors shall make certain that each new or transferred employee is instructed
in the safe practices pertaining to his or her work.
Supervisors shall ensure that the appropriate employees receive instruction in appropriate
emergency techniques, such as CPR, first aid, pole top, and confined space rescue, warranted
by the employee's duties.
1. Provide instructions on safe practices for the crew and see that they are followed.
2. Periodically examine supervised employees on their knowledge of the safety rules
and approved emergency techniques.
3. Not allow a worker to perform any task that cannot be performed safely or for which
the worker is not qualified.
4. Report every injury in the established manner prescribed for the facility.
5. Be responsible for the care and proper use of all protective devices.
6. Be responsible for proper posting of hazardous work areas as a safeguard to those
supervised. Under no circumstances shall the supervisor allow work to continue if safety
precautions are ignored.
7. Designate a qualified worker to be in charge of work during the supervisor's absence.
The supervisor should not leave the job while dangerous work is in progress.
8. Coach and direct employees who are working near exposed, energized wires, equipment,
9. Prescribe, along with employees, the appropriate PPE when establishing safety related
Employees shall be trained in and familiar with the safety-related work practices,
safety procedures, and other safety requirements in this section that pertain to their
respective job assignments.
Employees shall also be trained in and familiar with any other safety practices, including
applicable emergency procedures that are not specifically addressed in this section but
are related to their work and necessary for their safety.
1. The skills and techniques necessary to distinguish exposed live parts from other
parts of electrical equipment.
2. The skills and techniques necessary to determine the nominal voltage of exposed
3. The skills and techniques necessary to determine the minimum approach distances
corresponding to the voltages to which they are exposed.
4. The proper use of the special precautionary techniques, personal protective equipment,
insulating and shielding materials, and insulated tools for working on or near exposed
energized parts of electrical equipment.
Training may consist of a combination of classroom and on-the-job type.
The employee in charge shall conduct a job briefing with the employees involved before
the start of each job. The job briefing will at least cover the following subjects: hazards
associated with the job, work instructions involved, special precautions, energy source
controls, and personal protective equipment requirements.
If the work or operations to be performed during the work day are repetitive and similar,
at least one job briefing shall be conducted before the start of the first job of each
day or shift. Additional job briefings shall be held if significant changes, which might
affect the safety of the employees, occur during the course of the work. A brief discussion
is satisfactory if the work involved is routine and if the employee, by virtue of training
and experience, can reasonably be expected to recognize and avoid the hazards involved
in the job. A more extensive discussion shall be conducted if the work is complicated
or extremely hazardous, or the employee cannot be expected to recognize and avoid the
hazards involved in the job.
An employee working alone need not conduct a job briefing. However, the employee shall
ensure that the tasks to be performed are planned as if a briefing were required.
Employees shall wear appropriate personal protective equipment (PPE) and protective
clothing (see Section 7.4.8) to protect them from hazards of high-voltage apparatus.
Employees authorized or required to work on high-voltage systems shall be completely
familiar with the PPE and protective clothing they need for adequate protection while
working on such systems. (Refer to Appendix C for suggested types of PPE and protective
clothing.) (See Figure 7-1)
Employees should wear shoes or boots that comply with the requirements of ANSI Z41.
No metal parts shall be present in the sole or heel of the shoes where nonconductive
shoes are required.
Workers should wear approved hardhats when working aboveground on poles, structures,
or buildings or in trees.
Workers shall wear hardhats when working on the ground near poles, structures, buildings,
or trees in which work is being done. Workers shall wear hardhats when visiting or observing
in areas where overhead work is being done.
Figure 7-1. Appropriate personal protective equipment and protective clothing shall
be worn by electrical workers to protect them from electrical hazards.
7.4.3 EYE PROTECTORS
Whenever eyes are in danger of being injured, workers shall wear safety goggles or
other eye protectors meeting ANSI standards. When the work being performed dictates,
workers should wear nonmetallic and nonconductive eye protection. Appropriate PPE is
needed to protect workers from arc flash hazards.
7.4.5 METAL FASTENERS
Workers shall not wear articles such as loose chains, keys, watches, or rings if such
articles increase the hazards associated with inadvertent contact with energized parts
or can become caught under or snagged while climbing off or on structures, equipment
7.4.6 WORK GLOVES
When insulated gloves suitable for high-voltage are not required, otherwise suitable
work gloves should be worn while handling materials and equipment to prevent the possibility
of slivers, cuts, and skin irritation.
7.4.7 WORK CLOTHES
Work clothes should be made of natural materials, such as cotton or wool, or fire
resistant materials and should have full length sleeves. Sleeves should be rolled down
for greatest protection.
7.4.8 FIRE-RESISTANT (FR) CLOTHING
FR materials, such as flame-retardant treated cotton, meta-aramid, para-aramid, and
polybenzimidazole (PBI) fibers provide thermal protection. These materials can ignite
but will not continue to burn after the ignition source is removed. FR fabrics can reduce
burn injuries during an arc flash blends, para-aramid adds strength to a fabric to prevent
the fabric from breaking open due to the blast shock wave and high thermal energy of
All fire resistant fabrics comply with 29 CFR 1910.269(1)(6)(iii). Untreated cotton
and wool comply if the fabric will not ignite and continue to burn under the conditions
to which the employee could be exposed. ASTM F1506-94 and 2 new ASTM provisional standards,
outline the testing procedures to determine how various fabrics react in the presence
of an electric arc on an instrumented manikin or panel. The new ASTM provisional standards
provide testing procedures that expose untreated and fire resistant fabrics to electric
arcs. F1506-94 provides testing procedures that expose these same fabrics to a vertical
flame test. Also see NFPA 70E, 110.7(A) for details on flash hazard analysis.
22.214.171.124 ELECTRIC ARC HAZARDS
Electric shock is a widely recognized hazard and involves current flow through or
on the body. Burns from electric arcs are not as well recognized. There is no contact
required and the burns can be severe if the clothing ignites or melts. The hazards to
which the employee is exposed also include the clothing breaking open due to the arc
pressure blast, the heat from the electric arc and subsequent secondary fires or explosions.
The extent of the employee's injury is dependent on the length of the arc gap, available
fault current, duration of the arc, the distance of the employee from the arc, percentage
of the body burned, the employees age, medical condition, and number of layers of the
clothing system. The proper clothing system will minimize or reduce the burn injury.
126.96.36.199 TYPES OF FIRE RESISTANT FABRICS
Chemically dependent fire resistant fabrics are treated with flame retardant chemicals
added to the fiber or treatments applied to the fabric. These treatments are activated
by heat and produce gases that smother the flame. Typically, these fabrics have a definite
life as defined by the manufacturer. This is usually defined by the number of home or
commercial washings the garment is exposed.
Inherently fire resistant fabrics, by their composition, do not burn in air. The fire
resistance of this fabric is not affected by washing.
188.8.131.52 CLOTHING SYSTEMS
All clothing worn by affected workers should be considered part of the employees protective
clothing system. This includes rainwear, cold weather wear and underclothing. Protective
clothing should provide a good functional fit to increase the protection and comfort
of the clothing. When required, protection can be increased by wearing single or multiple
layers of flame-resistant outer garments over nonmelting clothing. Sleeves and shirts
should be fully buttoned and appropriate neck, head, and hand coverings provided.
7.4.9 RUBBER GLOVES
The following requirements apply:
1. Rubber gloves shall be of appropriate voltage rating for the work being performed.
All rubber gloves shall meet the standards set forth by ANSI/ASTM.
2. Rubber gloves issued for service shall be tested at appropriate voltage levels
at intervals not exceeding 6 months.
3. Leather glove protectors shall be worn over rubber gloves except where leather
protectors are not required by 29 CFR 1910.137 or the appropriate ASTM standard.
4. Rubber gloves should be carried cuff down in a bag, box, or container that is designed
for this purpose. Rubber gloves may be kept inside of leather protectors.
5. Rubber gloves shall be visually inspected and field air-tested before use each
day and at other times if there is cause to suspect damage.
6. Rubber gloves should be uniquely identified (i.e., serial number or other marking).
The results of dielectric tests should be documented.
7. Rubber gloves shall be wiped clean of any oil, grease, or other damaging substances
as soon as possible.
7.4.10 RUBBER LINE HOSE, HOODS, COVERS, SLEEVES, AND BLANKETS
Linemen's rubber insulating sleeves are worn to provide protection from electric shock
and burn to the arm and shoulder areas. They are available in several different thicknesses,
lengths, and designs, depending on the maximum voltage they are designed to protect against.
Insulating line hose (flexible hose) is used as an insulating cover for electric conductors
to protect against accidental contacts. A lengthwise slit with overlapping sides permits
the hose to be placed on conductors easily. It is available in various diameters, lengths,
and compositions. Insulating covers are used in conjunction with line hose to cover an
insulator and the conductor attached to it for protection against accidental contact.
Rubber insulating blankets are molded sheets of insulating rubber or synthetic elastomer,
usually square or rectangular in shape, designed to cover energized electrical equipment
to prevent direct accidental contact by electrical workers.
7.4.11 LIVE LINE TOOLS
A careful periodic inspection shall be made of equipment used for handling or testing
energized lines or equipment. Such tools shall be examined before each use to make certain
they are in good condition.
Particular attention shall be given to preserving the surfaces of wooden and fiberglass
tools used around electrical equipment, including ladders, pike poles, switch sticks,
live-line tools, and insulating platforms. Only colorless varnish or other appropriate
transparent insulating preservative shall be used.
Insulated tools shall be stored in a dry location. Suitable containers or racks shall
be provided to protect the tools from mechanical damage and warping.
7.4.12 STOREROOM STORAGE
Since heat, light, oil, and distortion are natural enemies of rubber, rubber protective
equipment should be guarded from these as much as possible. Rubber equipment shall not
be stored near boiler rooms, steam pipes, or radiators and should be protected from exposure
to direct sunlight.
Gloves should be stored in their natural shape in the leather protector. Keep sleeves
flat with the inserts left in. Blankets should be stored flat, hung on pegs by the eyelet
or rolled up. Line hose should be stored in its natural shape.
7.4.13 TRUCK STORAGE
The storing of rubber protective equipment on the truck should be planned. If possible,
separate compartments should be provided for each class of equipment, and each compartment
should be of sufficient size to allow the articles to lie in a natural position. Rubber
gloves should be stored in glove bags and hung up. If stored in tool bags or inside boxes,
nothing should be piled on top to cause distortion. Gloves should not be stored near
Sleeves should be stored flat with inserts rolled up lengthwise, or placed in a tube
shaped bag. Nothing should be placed on top of sleeves or stored near vehicle heaters.
7.4.14 PLACING OF INSULATING GOODS ON CONDUCTORS
When workers are about to begin work that requires the use of rubber goods, they should
climb or raise the bucket to a position just below the first line of conductors. When
climbing they should then determine their working position and what lines and other conductors
should be covered. They should then request the required rubber goods. Before proceeding
further, the workers shall put on the rubber gloves and leather protectors and make certain
that they are in good order. Rubber goods shall be raised in a secure manner.
As the workers ascend to their working position, they shall cover all conductors which
provide a hazard. This should be done from below whenever possible. At no time shall
workers pass through energized equipment before it is covered with rubber goods (line
guards). All conductors and grounds adjacent to working space shall be considered, including
those near any possible change of position that may be necessary. When line hose is applied
to vertical or sagging wires, it should be fastened to the line to prevent its slipping
from position. When blankets are used for covering items such as dead ends, potheads,
secondary racks, and transformers, they should be secured by wooden or plastic clamp
pins or tie thongs. After the protective equipment has been placed, care should be taken
to prevent damage to the rubber from tie wires, spurs, or other objects.
7.4.15 REMOVING INSULATING GOODS FROM CONDUCTORS
When the job is completed, the protectors should be removed in the reverse order of
installation. Remote conductors are removed first and the wires nearest the workers last.
After being detached, the equipment should immediately be lowered to the ground.
7.4.16 CLEANING AND INSPECTING
After the rubber goods have been lowered to the ground, they should be cleaned and
visually inspected before being placed in the carrier compartments of the truck.
7.5 PROTECTIVE GROUNDING OF LINES AND EQUIPMENT
Grounding is the most effective way of protecting electrical workers from electric
shock. That is why it is important to ensure that all deenergized lines and equipment
Blankets should be rolled up and placed in canisters or protective canvas holders.
Do not fold, hold together with tape, pile materials on top of, or store blankets near
vehicle heaters. This section provides information concerning protection for workers
repairing, servicing, or working on high-voltage power lines.
Figure 7-2. Equipotential grounding is the most effective way of protecting employees
who are working on high-voltage systems and equipment.
184.108.40.206 REDUCE THE POTENTIAL VOLTAGE DIFFERENCES ACROSS THE WORKER
The primary function of personal protective grounds is to provide maximum safety for
personnel while they are working on deenergized lines or equipment. This will be accomplished
by making provisions that will reduce the potential voltage differences at the work site
(voltage differences across the worker) to a safe value in the event that line or equipment
being worked on is accidentally reenergized, voltages induced from other energized lines,
an energized line falls on the line being worked, or there is a lightning strike near
the line being worked.
The personal protective grounds should provide a low-impedance path to ground to ensure
prompt operation of the circuit protective devices.
Certain methods and steps should be exercised when placing grounds and loads to protect
workers from high-voltage hazards.
220.127.116.11 DEENERGIZED LINES
When an energized line or equipment in excess of 600 V is removed from service to
be worked on, it shall be treated as energized until it is deenergized, tagged, locked
if necessary, tested, and grounded.
Figure 7-2. Equipotential grounding is the most effective way of protecting employees
who are working on high-voltage systems and equipment.
18.104.22.168 NEW CONSTRUCTION OR DISMANTLING OF FACILITIES
If isolating devices are not in place and energization is impossible from any source,
single-phase grounding is appropriate, acceptable, and safe. If energization is possible
by the closure of a jumper or isolating device, shorts and grounds shall be used unless
conductor handling activity makes this impractical or impossible because of line design
or construction process.
22.214.171.124 MINIMUM APPROACH DISTANCE FROM UNGROUNDED CONDUCTORS
The minimum approach distances in Section 126.96.36.199 shall be maintained from ungrounded
conductors at the work location. The ground may be omitted if the making of the ground
is impractical or the resulting conditions are more hazardous than working on the lines
or equipment without grounding. However, all work shall be done as if the line or equipment
188.8.131.52 VISIBLE THREE-PHASE SHORT AND GROUND REQUIRED
Visible three-phase short circuiting may be accomplished through conductive parts
such as guy wires and unpainted metal tower members, but shall not be effected through
a grounding mat or other concealed conductors.
184.108.40.206 GROUND CIRCUIT
No power disconnect switch, power circuit breaker, transformer, wave trap, or fuse
shall be part of the protective grounding circuit.
Table 7-2. AC live-line work minimum approach distance.
Note 1: These distances take into consideration the highest switching surge an employee
will be exposed tto on any system with air as the insulating medium and the maximum voltage
Note 2: The clear live line tool distances shall equal or exceed the values for the
indicated voltage ranges.
Note 3: See 29 CFR 1910.269, Appendix B for information on how the minimum approach
distances were derived.
7.5.3 GROUNDING EQUIPMENT
ASTM Committee F-18, Electrical Protective Equipment for Workers, has developed and
published a consensus standard for protective grounds, ASTM Designation: F-855. This
voluntary consensus standard may be used by all Federal agencies for procurement purposes.
Therefore, grounding cables, clamps, and ferrules purchased should meet all the requirements
of ASTM Designation: F-855. Aluminum cables shall not be used for personal grounds. The
grounding of high-voltage lines and equipment will provide workers with additional protection
from electric shock if grounds are sized, selected, and installed properly.
Grounding cables shall be available for use when work is being done on deenergized
lines or equipment.
220.127.116.11 APPROVED CAPACITY
Grounding cables shall accommodate the maximum fault current to which the cable or
equipment might be subjected.
18.104.22.168 GROUNDING CABLES AND HARDWARE
Personal protective grounding cables consist of appropriate lengths of suitable copper
grounding cable, with electrically and mechanically compatible ferrules and clamps at
each end. In addition, appropriate hot sticks are required for installing and removing
the conductor-end clamps to the conductors. Hot sticks are required for attaching ground-end
clamps if the grounded system and the worker are at different potentials. Cluster bars
provide a low resistance means of connecting the ground-end clamps. Each of these components
will be discussed in the following subsections.
22.214.171.124 GROUNDING CABLES
Most of the grounding cables in use today (and available for purchase) are actually
manufactured for another purpose-principally as welding cable. These extra-flexible copper
cables with jackets are manufactured according to appropriate ASTM standards for both
cables and jackets, and can be expected to perform satisfactorily as grounding cables.
There are several classes of flexible cable with various stranding in the sizes normally
used for grounding cables.
Welding cables are nominally insulated at 600 volts. When used as grounding cable,
the insulation or jacket serves primarily for mechanical protection of the conductor.
The flexible elastomer or thermoplastic jackets are manufactured, applied, and tested
according to ASTM standards. Black, red, and yellow jackets are usually neoprene rubber
compounds, while clear jackets are ultraviolet-inhibited polyvinyl chloride (PVC). All
jackets should have the AWG size stamped or printed repeatedly along the length of the
cable. The clear jacket allows easy visual
inspection of the conductor for strand breakage, but becomes stiff and hard to handle
at low temperatures. The clear jacket will split or shatter at very low temperatures.
Ferrules should be threaded-stud copper base compression type. Ferrules should have
the filler compound vent hole at the bottom of the cable so that employees can visually
check that the cable is fully inserted into the ferrule. Compound should be used with
crimped ferrules. The ferrules should be crimped with the ferrule manufacturer's recommended
die. The press shall have enough pressure to completely close the die. The area covering
the inserted cable jacket should not be compressed. Heat shrink or springs should be
installed over a portion of the ferrule to minimize strand breakage caused by bending.
In all cases, the manufacturer's recommendations should be followed.
126.96.36.199.4 HANDLING OF GROUNDING CABLE
Personal protective grounds are usually handled and lifted by the cable. However,
continuous flexing eventually breaks the conductor strands beneath the jacket. Therefore,
employees should minimize the use of sharp bends in the cable.
188.8.131.52.5 SIZE OF GROUNDING CABLE
The size of the grounding cable must be selected to handle the maximum calculated
fault current of the power system or specific portion thereof. The minimum size that
shall be used for grounding cables is #2 AWG flexible copper. In larger substations,
the maximum available fault current may require larger cables. If larger cables are not
available, parallel cables (with the appropriate derating factor) may be used. Most manufacturers
and suppliers of grounding cables publish tables to assist the user in selecting the
proper cable size for a given fault current. These tables show the maximum fault current
capability for several sizes of copper grounding cables. 184.108.40.206.6 GROUNDING CABLE LENGTH
Excessive cable lengths should be avoided. Therefore, slack in the installed cables
should be minimal to reduce possible injury to workers. Resistance in the cable increases
with cable length, and excessive length could exceed the tolerable voltage drop across
the body. Longer than necessary cables also tend to twist or coil, which reduces the
effectiveness of the cable.
220.127.116.11.7 GROUNDING CLAMPS
Grounding clamps are normally made of copper or aluminum alloys; sized to meet or
exceed the current-carrying capacity of the cable; and designed to provide a strong mechanical
connection to the conductor, metal structure, or ground wire/rod.
18.104.22.168.7.1 CLAMP TYPES
Clamps are furnished in, but not limited to, three types according to their function
and methods of installation:
1. Type I clamps, for installation on deenergized conductors, are equipped with eyes
for installation with removable hot sticks.
2. Type III clamps, for installation on permanently grounded conductor or metal structures,
have T-handles, eyes, and/or square-or hexagon-head screws.
3. Other types of special clamps are designed for specific applications, such as cluster
grounds, underground equipment grounding, and so on.
22.214.171.124.7.2 CLAMP JAWS
Bus clamps should be furnished with smooth jaws for installation on copper, aluminum,
or silverplated bus work without marring the surface. Conductor or metal structure clamps
should be furnished with serrations or cross-hatching designed to abrade or bite through
corrosion products on surfaces of the conductor or the metal structure being clamped.
Several styles of conductor and ground-end clamps have jaws that can be replaced when
the serrations have worn. Self-cleaning jaws are recommended for conductor-end clamps
used on aluminum or aluminum conductor steel reinforced (ACSR) conductors. Several styles
of ground-end clamps are designed with a cup-point set screw which should be tightened
with a wrench (after the serrated jaws have been securely tightened) to break through
paint, rust, galvanized coating, or corrosion on the surface that is to be clamped.
A typical grounding cable for transmission line work used by line crews consists of
a 2/0 AWG copper cable with an insulating jacket, terminated with an all-angle, self-cleaning
aluminum conductor clamp at one end, and a flat-faced clamp with a set screw at the other
end for connecting to a tower leg or ground wire/rod.
126.96.36.199.8 GROUNDING CLUSTER BARS
When climbing wood-pole structures, workers may use a grounding cluster bar to connect
the phase cables to the pole ground wire, if the ground wire has sufficient capacity
to carry the fault current. Cluster bars must have an attached bonding lead. If there
is no pole ground wire, the cluster bar for each pole is connected to a common driven
or screw-in ground rod with a grounding cable (or cables). In substation grounding, a
copper bar is sometimes used to connect the three-phase cables and a fourth cable to
a riser from the station ground mat. When installing personal grounds on wood structures
from a bucket, the ground cables may be connected between the overhead ground wire (OGW),
and the phases without the use of cluster bars provided that an electrical bond of sufficient
current carrying capacity exists between the OGW and the structure ground.
188.8.131.52.9 TEMPORARY GROUND RODS
Some typical examples of temporary ground rods used for grounding ungrounded structures
or mobile equipment, or during conductor splicing operations, are either:
1. A minimum ⅝-inch diameter bronze, copper, or copper-weld rod at least 6 feet long,
driven to a depth of at least 5 feet; or
2. A 6-foot, screw-type ground rod, consisting of a minimum ⅝-inch diameter copper-weld
shaft with a bronze auger bit and bronze T-handle, screwed to a depth of at least 5 feet
(preferred). The T-handle must be tightly connected to the rod.
If a temporary rod cannot be driven or screwed to a depth of 5 feet, additional rod(s)
should be driven or screwed so that a total of at least 5 feet of rod is buried. These
rods shall be bonded
together with grounding cables prior to installing phase grounds. The rods should
be placed 6 to 8 feet apart; however, the 10-foot clearance from the rods should be maintained.
OGWs may be used at any time to bond the conductors provided that these wires are electrically
bonded to the structure ground, either permanently or by personal grounds.
Groundsmen should stay clear (at least 10 feet where feasible) of items such as down
guys, ground rods, maintenance vehicles, and structure legs or ground wires while they
are bonded to protective grounds which are in place. When it is absolutely necessary
to work on or near these features, employees should use bonded conductive or insulated
platforms, or approved insulated shoes to minimize the hazard from step and touch potentials.
7.5.4 TESTING BEFORE INSTALLING GROUNDS
Before grounds are installed, the deenergized line or equipment shall be tested for
voltage. Appropriate testers for the nominal voltage involved (audio or visual) should
be used. They shall be tested immediately before and after use to verify that they are
in good working condition. 7.5.5 ATTACHING AND REMOVING GROUNDS
Employees attaching and removing grounds shall comply with the following:
1. Grounding equipment should be visually inspected and all mechanical connections
checked for tightness before each use.
2. The surface to which the ground is to be attached should be clean before the grounding
clamp is installed or a self-cleaning clamp shall be used.
3. No ground shall be removed until all personnel are clear of the temporary grounded
lines or equipment. When the grounding set is removed, it shall be disconnected from
the line or equipment end first with an approved hot-line tool and moved to a point clear
of energized conductors before the ground end is disconnected.
7.5.6 GROUNDING METHODS AND LOCATION OF GROUNDS IN ORDER OF PREFERENCE
Employees installing grounds shall install them using the information given in the
184.108.40.206 WORK LOCATION
Grounds should be installed at the work location with all grounded parts of different
potential bonded together (on wood poles, all down guys, overhead ground wire, neutral
conductor, and pole ground). The cluster bar assembly should be installed below the working
area and jumper to the ground point or the neutral conductor and the phase conductor,
a method of grounding termed "equipotential" grounding. It provides the greatest margin
of safety for the lineworker by placing everything at equal potential, eliminating the
possibility of the lineworker getting in series to ground.
220.127.116.11 MULTIPLE WORK LOCATIONS AND SINGLE-PHASE GROUNDING AT WORK LOCATION If work
is to be performed at more than one place in a line section, the line section shall be
grounded at one location and the conductor be grounded at each work location to reduce
the potential voltage difference across the work site.
18.104.22.168 OTHER LOCATIONS
Grounds shall be placed at the work location or at each side of the work location
and as close as practical to it.
7.5.7 TESTING WITHOUT GROUNDS
Grounds may be temporarily removed when necessary for testing. Each employee shall
use insulating equipment and be isolated from any hazard involved. Additional measures
may be necessary to protect each exposed employee in case previously grounded lines or
equipment become energized.
7.5.8 GROUND PERSONNEL
In cases where ground rods or pole grounds are used for personal protective grounding,
personnel working on the ground shall either maintain a safe distance from such equipment
or use the appropriate equipment designed to prevent touch-and-step potential hazards.
The term "touch potential hazard" refers to the difference in voltage measured between
the grounding equipment and a worker in contact with the grounding equipment at the time
it is accidentally energized. The term "step potential hazard" refers to the difference
in voltage measured between each foot of the worker standing or walking in an electrical
field created by high voltage brought to earth.
7.6 INSTALLING OR REMOVING CONDUCTORS
Employees installing or removing conductors should follow certain guidelines to ensure
7.6.1 WORKING ON ENERGIZED LINE OR EQUIPMENT
Employees working on energized lines or equipment should comply with the following:
1. Work on electrical equipment and circuits other than electrical utility lines and
equipment, operating a 50 V or more ground, should be worked on following the guidelines
of Section 2 of the handbook.
2. Line or equipment carrying an ac voltage in excess of 600 V phase-to-phase should
be worked on with rubber gloves or live line tools. All other necessary protective devices
such as line hose, hoods, covers, sleeves, and rubber blankets should be used. (See Section
3. Energized line should be worked on from below whenever possible. When working energized
line or equipment carrying 600 V or more to ground, there shall be two qualified workers
performing the work (see Section 2.1.2). Work shall not be performed on energized
lines or equipment during rain, snow, sleet, fog, and other damp conditions, except
in extreme emergencies if in the opinion of supervision and line crew it can be done
4. While working on the same pole, workers shall not work simultaneously on wires
that have a difference of potential.
5. Rubber gloves of appropriate voltage rating shall be worn when working within reach
of a fellow employee who is working on or within reach of wires or equipment carrying
voltage in excess of 600 V.
6. Insulated tongs or disconnect sticks shall be used to open or close plugs or fuses
or to disconnect blades.
7.6.2 STRINGING OR REMOVING DEENERGIZED CONDUCTORS
Employees stringing or removing deenergized conductors should follow certain safe
work practices. Consideration should be given to the following:
1. When it is necessary to conduct any work on poles or structures carrying more than
one circuit and where there is not safe working clearance between circuits, the conductors
not being worked on shall be either:
a. Untied and separated with proper clearance from the pole or structure, b. Deenergized
and grounded, or c. Covered with the necessary protective devices.
2. Prior to stringing operations, a job briefing shall be held setting forth the plan
of operation and specifying the type of equipment to be used, grounding devices to be
used and instructions to be followed, crossover methods to be employed, and clearance
3. Where there is a possibility that the conductor will accidentally contact an energized
circuit or receive a dangerous induced voltage buildup, to protect the employee from
the hazards of the conductor, the conductor being installed or removed shall be grounded
or provisions made to insulate or isolate the employee.
4. If the existing line is deenergized, proper clearance authorization should be secured
and the line grounded on both sides of the crossover, or the line being strung or removed
should be considered and worked on as energized.
5. When workers cross over energized conductors, rope nets or guard structures shall
be installed unless provisions are made to isolate or insulate the workers or the energized
conductor. Where practical, the automatic reclosing feature of the circuit-interrupting
device should be made inoperative. In addition, the line being strung should be grounded
on either side of the crossover or considered and worked on as energized.
6. Conductors being strung or removed should be kept under positive control by the
use of adequate tension reels, guard structures, tielines, or other means to prevent
accidental contact with energized circuits.
7. Guard structure members should be sound, of adequate dimension and strength, and
8. Catch-off anchors, rigging, and hoists should be of ample capacity to prevent loss
9. The manufacturer's load rating should not be exceeded for stringing lines, pulling
lines, sock connections, and all load-bearing hardware and accessories.
10. Pulling lines and accessories should be inspected regularly and replaced or repaired
when damaged or when their dependability is doubtful.
11. Conductor grips should not be used on wire rope unless designed for this application.
12. While the conductor or pulling line is being pulled (in motion), workers should
not be permitted directly under overhead operations, nor should any employee be permitted
on the cross arm.
13. A transmission clipping crew should have a minimum of two structures clipped between
the crew and the conductor being sagged. When working on conductors, clipping crews should
install grounds at the work location. The grounds should remain intact until the conductors
are clipped in, except on dead-end structures.
14. Except during emergency restoration activities, work from structures should be
discontinued when adverse weather (such as high wind or ice on structures) makes the
15. Stringing and clipping operations should be discontinued during an electrical
storm in the immediate vicinity.
16. Reel-handling equipment, including pulling and braking machines, should have ample
capacity, operate smoothly, and be leveled and aligned in accordance with the manufacturer's
17. Reliable means of communication between the reel tender and pulling rig operator
should be provided.
18. Each pull should be snubbed or dead-ended at both ends before subsequent pulls.
7.6.3 STRINGING ADJACENT TO ENERGIZED LINES
Employees stringing adjacent to energized lines should follow certain safe work practices.
Consideration should be given to the following:
1. When performing work from structures, clipping crews and all others working on
conductors, subconductors, or overhead grounding conductors should be protected by individual
grounds installed at every work location.
2. When workers are stringing adjacent to energized lines, the tension-stringing method
or other methods that prevent unintentional contact between the lines being pulled and
any worker should be used.
3. All pulling and tensioning equipment should be effectively grounded.
4. A ground should be installed between the tensioning reel setup and the first structure
to ground each bare conductor, subconductor, and overhead grounding conductor during
stringing across or adjacent to energized lines.
5. During stringing operations, each bare conductor, subconductor, and overhead grounding
conductor should be grounded at the first tower adjacent to both the tensioning and pulling
setup and at appropriate intervals. The grounds should be left in place until conductor
installation is completed. Except for moving-type grounds, the grounds should be placed
and removed with a hot stick.
6. Conductors, subconductors, and overhead grounding conductors should be grounded
at all dead-end or catch-off points.
7. A ground should be located at each side and within 10 ft. of working areas where
conductors, subconductors, or overhead grounding conductors are being spliced at ground
level. The two ends to be spliced should be bonded to each other. It is recommended that
splicing be carried out on either an insulated platform or on a conductive metallic grounding
mat bonded to both grounds. When a grounding mat is used, it should be roped off and
an insulated walkway provided for access to the mat.
7.7 SPECIAL TOOLS
Line workers shall be familiar with special tools that are used for climbing, such
as climber gaffs, climber straps, and body belts shall properly store and maintain such
7.7.1 LINEWORKERS’ CLIMBING TOOLS
Employees should apply the following:
1. All climbers should be inspected frequently by the worker using them.
2. Climber gaffs should be kept sharp.
3. A climber shall not be used when its gaff becomes shorter than 1-1/4 in. inside
4. Climber straps that are worn or otherwise defective shall be replaced.
7.7.2 BODY BELTS AND SAFETY STRAPS
Employees using body belts and safety straps (work positioning equipment) should apply
1. All body belts and safety straps shall be inspected before each use by the employee
who uses them.
2. Workers shall use their body belts and safety straps when doing any work involving
danger of falling.
3. Body belts and safety straps should not be stored with unguarded sharp tools or
Figure 7-3. Employees using special tools for climbing and for servicing high voltage
systems shall be trained on how to use such tools and equipment.
4. Heat, sharp bends, and overstressing of body belts and safety straps should be
avoided as they are injurious to leather. Wet leather should be dried slowly at moderate
7.7.3 TOOL BAG AND EQUIPMENT
Tools, small equipment, and materials should be raised and lowered in a tool bag.
The tool bag should be inspected before use to see that it contains no broken glass or
other material on which the employee could cut his or her hand or rubber gloves. Tool
bags should not have any metal in their construction.
7.7.4 TAPES AND RULERS
Workers should not use metal measuring tapes or tapes having metal strands woven into
the fabric, brass bound rules, or metal scales when working near electrical equipment
7.7.5 SPOON AND SHOVELS
Tools of this type, especially those having long wooden handles, shall not be used
when the handles are cracked, split, or broken.
Figure 7-3. Employees using special tools for climbing and for servicing high voltage
systems shall be trained on how to use such tools and equipment.
7.7.6 PIKE POLES
Pike poles shall comply with the following:
1. Cracked, broken, or slivered pike poles should not be used;
2. Pike poles should not be thrown; and
3. When not in use and loaded on the truck, the points should be protected so that
they will not injure anyone.
7.7.7 HAND AXES AND SHARP TOOLS
Hand axes and sharp tools shall comply with the following:
1. Hand axes should not be used on overhead work; and
2. When not in use, sharp tools should be protected by the suitable guards or containers.
7.7.8 HANDLINES AND TAGLINES
Use high quality, nonconductive hand lines and taglines. Keep them stored in a clean,
dry location and protected from damage and contamination. Wear clean gloves when handling
hand lines and taglines to avoid contaminating the rope. Remove wet, dirty, or damaged
ropes from service.
7.8 TREE TRIMMING
Equipment used to trim trees shall be maintained in approved and proper working condition
to aid tree trimmers and protect them from hazards.
7.8.1 CARE AND USE OF TOOLS
Tools shall be cared for using the following methods:
1. The handles of all tree-trimming tools shall be kept well dressed and varnished.
2. When trimming trees near live conductors, the employee shall not work with wet
tools or ropes. Such equipment should be protected during rain showers.
3. A tree-trimming saw shall be protected by being put into its scabbard when it is
not in use.
4. All ropes shall be inspected frequently for cuts and wear.
The following shall be applied for climbing:
1. An employee should use a ladder to climb a tree, unless the employee is properly
equipped and trained for tree climbing.
2. Climber gaffs and straps shall be designed for tree climbing. The safety strap
shall be constructed to withstand contact with saws and other sharp objects. Workers
in trees shall be tied off.
7.9 SERIES STREET-LIGHTING CIRCUITS AND APPARATUS
Lighting circuits and apparatus used for series street-lighting should comply with
1. Rubber gloves or any other necessary protective equipment should be used when working
on a series street-lighting circuit, unless the circuit is electrically isolated and
grounded at the work location. Unless properly tagged and isolated, series street lighting
circuits should be considered as being energized.
2. The opening of a time clock, a photoelectric relay, or remote control overcurrent
control equipment shall not be considered as isolation points that provide a safe work
condition while employees work on series lighting circuits.
3. The use of series lighting circuits is discouraged.
Underground work requires a means of safe entrance and exit from the workspace. Employees
should follow the guidance given in the following subsections to ensure safety in entering
and leaving such work spaces.
7.10.1 WORKING IN MANHOLES, UTILITY TUNNELS, AND VAULTS
Manholes, utility tunnels, and vaults may be considered confined spaces and shall
comply with 29 CFR 1910.146,1910.269(e) and (t), and 1926.956. The following may apply
to employees working in manholes, utility tunnels, and vaults:
1. Employees who enter manholes shall be trained in the hazards of the confined spaces,
confined space entry procedures, and confined space emergency and rescue procedures.
2. When opening a manhole, employees shall completely remove the manhole cover from
the opening. Manhole covers should be removed before the cable is rodded or installed
3. Open manholes shall be barricaded and protected by flags or guards as required.
All open manholes shall be protected as required by 29 CFR 1910.269(e).
4. Before the pit is entered, it shall be tested for oxygen content and the flammable-gas
explosive limit. Workers shall not smoke or use an open flame while tests for an explosive
mixture of gas are being made.
5. If the oxygen level is less than 19.5 percent or greater than 21 percent, the pit
shall be ventilated and retested before any work begins.
6. If the flammable-gas content is more than 10% of the lower explosive limit, the
pit shall be ventilated and retested before any work begins. When testing indicates that
a manhole contains either a mixture of explosive gas and air richer than safe working
flammable liquids, corrective measures shall be taken before work in the manhole
is allowed to proceed.
7. When nitrogen is used in manholes or confined areas, approved atmosphere testing
devices shall be placed in operation where they can be observed by people in the manhole.
When the testing devices show a deficiency of oxygen, all personnel shall leave the manhole
until the proper atmosphere is restored.
8. The manhole shall be ventilated continuously when occupied.
9. An attendant is required topside with the means to summon help without leaving
his or her station. The attendant shall be capable of instituting a rescue without entering
the manhole. The attendant on the surface is responsible for the safety of the persons
in the manhole.
10. The topside attendant can perform other duties outside of the enclosed space if
these duties do not distract the attendant from monitoring employees within the space.
All manholes over 4 ft. deep should be entered with the use of a ladder as required by
29 CFR 1910.269 (t)(1).
11. Workers should open all entrance bars or chains on the topside of manhole guards
before entering or leaving a manhole. All chains or bars should be closed at all other
times, except when raising or lowering tools or materials.
12. Operations involving chemical cleaning agents, solvents, volatile chemicals, cutting
and welding equipment, and other hazardous agents or tools require additional consideration.
Consultation with and concurrence of appropriate industrial safety and industrial hygiene
personnel are required.
13. The employee shall enter or leave a manhole by means of a ladder. The employer
shall not use a cable, cable hanger, or manhole rack as a support for climbing. A manhole
ladder should never be removed while a worker is in the manhole unless absolutely necessary.
In the instance of a ladder being removed to make it easier to rescue a worker, the topside
attendant shall fully devote his or her attention and efforts to instituting a rescue
using the worker's body harness and lifeline if necessary. The ladder shall be replaced
as soon as practical.
Note: The other workers in the hole should be warned that the ladder is to be removed
in time to allow him or her to exit the hole if necessary.
14. Materials, tools, and equipment should be kept at a sufficient distance from the
entrance to the manhole to avoid any hazard to the occupant from falling objects or from
hot metal or spilled compounds.
15. Blowtorches and furnaces should be ignited before being lowered into manholes
unless this creates additional hazards.
16. Rags, tape, refuse, and combustible and flammable materials should not be allowed
to accumulate in a manhole.
17. Instrumentation shall be calibrated per manufacturer's instructions. [See 29 CFR
1910.269(e)(8)]. A record of calibration should be maintained.
18. GFCIs shall be used for 120-V ac power unless such power is supplied by a portable
or vehicle-mounted two-wire, single-phase generator rated not more than 5 kW, where the
circuit conductors of the generator are insulated from the generator frame and all other
grounded surfaces. (See Section 6.4).
19. All cables and insulated wires that do not have grounded conducting sheaths or
shielding should be treated as bare conductors. They shall be considered energized unless
approved methods have been used to determine that they are deenergized. Barricade or
cover these conductors with protective equipment or devices that will be within reach
of a worker's position.
20. Where multiple cables are present the cable to be worked on shall be identified
by electrical means unless its identity is obvious. [See 29 CFR 1910.269(t)(5)]. Where
cable has one or more abnormalities that could be an indication of an impending fault,
the defective cable shall be deenergized, except when service load conditions and a lack
of feasible alternatives require that the cable remain energized. In that case, employees
may enter the manhole if they are protected by the affects of the failure by flash blankets
or other devices capable of containing the adverse effects of the fault. [See 29 CFR
7.10.2 WORKING ON ENERGIZED UNDERGROUND CABLES
In general, work should not be performed on energized underground cables. However,
strictly external work, not requiring an appreciable change in location of the cable,
may be performed under direct supervision. Energized cables that are to be moved shall
be inspected for defects. [See 29 CFR 1910.269(t)(6)].
7.10.3 TERMINALS OF UNDERGROUND CABLES (POTHEADS)
Before work is started, the overhead line connections to a cable terminal upon which
work is to be performed should be either:
1. Deenergized and grounded or
2. Disconnected and covered with protective equipment.
Ferro-resonance can generate overvoltages of up to 12 times line-to-ground source
voltage upon opening of a single-phase device or a poorly synchronized three-phase device.
Violent failure can occur, exposing personnel to the high-voltage failure and accompanying
conditions. Ferro-resonant conditions can result in damage to lightning arresters, switching
devices, buried cable, transformers, and associated equipment.
Ferro-resonance can be initiated when all of the following elements are present and
the switching means at dip point or takeoff is either a single-phase device or an unsynchronized
three-phase device that does not operate all phases within one-half cycle: i. System
grounded at the source but with no ground at the transformer bank, such as a transformer
or transformer bank connected delta on a grounded-wye system. ii. Shielded cable or overhead
conductor length sufficient to create the capacitance necessary.
iii. Transformer size that permits saturation of the iron core at the operating voltage
iv. Transformer unloaded or very lightly loaded.
Prevention or control of ferro-resonance may be accomplished by any of the following
1. Using a wye-wye transformer connection with both neutrals grounded and tied to
the system neutral.
2. Using only phase-to-neutral (not phase-to-phase) transformer connections for single-phase
3. Limiting length of underground cable between transformers and single-pole or poorly
synchronized three-pole switching devices.
4. If single-pole or poorly synchronized switching devices must be used, ensuring
that transformer and underground cable are loaded in excess of 2% resistive load of the
5. If transformer primary is ungrounded-wye, temporarily grounding the neutrals of
the transformers being switched.
6. Installing close-coupled, high-speed, three-pole switching devices to minimize
the duration of the single-phase condition during opening and closing of the circuit