NEETS Module 4—Introduction to Electrical Conductors, Wiring Techniques, and Schematic Reading
Pages i - ix
, 1-1 to 1-10
1-11 to 1-20
, 1-21 to 1-28
2-1 to 2-10
,2-11 to 2-20
2-21 to 2-30
, 2-31 to 2-40
2-41 to 2-53
, 3-1 to 3-10
3-11 to 3-20
, 3-21 to 3-24
to 4-10, 4-11 to 4-18, Index
SELECTION OF WIRE SIZE
Several factors must be considered in selecting the size of wire to be used for transmitting and
distributing electric power. These factors will be discussed throughout this section. Military specifications
cover the installation of wiring in aircraft, ships, and electrical/electronic equipment. These specifications
describe the technical requirements for material purchased from manufacturers by the Department of Defense. An
important reason for having these specifications is to ensure uniformity of sizes to reduce the danger of fires
caused by the improper selection of wire sizes. Wires can carry only a limited amount of current safely. If the
current flowing through a wire exceeds the current-carrying capacity of the wire, excess heat is generated. This
heat may be great enough to burn off the insulation around the wire and start a fire.
FACTORS GOVERNING THE CURRENT RATING
The current rating of a cable or wire indicates the current capacity that the wire or cable can safely
carry continuously. If this limit, or current rating, is exceeded for a length of time, the heat generated may
burn the insulation. The current rating of a wire is used to determine what size is needed for a given load, or
The factors that determine the current rating of a wire are the conductor size, the
location of the wire in a circuit, the type of insulation, and the safe current rating. Another factor that will
be discussed later in this chapter is the material the wire is made of. As you have already seen, these factors
also affect the resistance in ohms of a wire-carrying current.
increase in the diameter, or cross section, of a wire conductor decreases its resistance and increases its
capacity to carry current. An increase in the specific resistance of a conductor increases its resistance and
decreases its capacity to carry current.
The location of a wire in
a circuit determines the temperature under which it operates. A wire may be located in a conduit or laced with
other wires in a cable. Because it is confined, the wire operates at a higher temperature than if it were open to
the free air. The higher the temperature under which a wire is operating, the greater will be its resistance. Its
capacity to carry current is also lowered. Note that, in each case, the resistance of a wire determines its
current-carrying capacity. The greater the resistance, the more power it dissipates in the form of heat energy.
Conductors may also be installed in locations where the ambient (surrounding) temperature is relatively high.
When this is the case, the heat generated by external sources is an important part of the total conductor heating.
This heating factor will be explained further when we discuss temperature coefficient. We must understand how
external heating influences how much current a conductor can carry. Each case has its own specific limitations.
The maximum allowable operating temperature of insulated conductors is specified in tables. It varies with the
type of conductor insulation being used.
The insulation of a wire does not affect the resistance of the wire. Resistance does, however, determine how much
heat is needed to burn the insulation. As current flows through an insulated conductor, the limit of current that
the conductor can withstand depends on how hot the conductor can get before it burns the insulation. Different
types of insulation will burn at different temperatures. Therefore, the type of insulation used is the third
factor that determines the current rating of a conductor. For
instance, rubber insulation will begin deteriorating at relatively low temperatures, whereas varnished
cloth insulation retains its insulating properties at higher temperatures. Other types of insulation are
fluorinated ethylene propylene (FEP), silicone rubber, or extruded polytetrafluoroethylene. They are effective at
still higher temperatures.
SAFE CURRENT RATINGS
The National Board of Fire
Underwriters prepares tables showing the safe current ratings for sizes and types of conductors covered with
various types of insulation. The allowable current-carrying capacities of single copper conductors in free air at
a maximum room temperature of 30º C (86º F) are given in table 1-3. At ambient temperatures greater than 30º C,
these conductors would have less current- carrying capacity.
Table 1-3.—Temperature Ratings and Current-Carrying Capacities (in Amperes) of Some Single
Copper Conductors at Ambient Temperatures of 30ºC
Q11. List the four factors you should use to select wire for a specified current rating.
Q12. What are three types of nonmetallic insulating materials that can be used in a high-temperature
Q13. State why it is important for you to consider the ambient (surrounding) temperature
of a conductor when selecting wire size.
Although silver is the best conductor, its cost limits its use to special circuits. Silver is used where
substance with high conductivity or low resistivity is needed.
The two most commonly used
conductors are copper and aluminum. Each has positive and negative characteristics that affect its use under
varying circumstances. A comparison of some of the characteristics of copper and aluminum is given in table 1-4.
Table 1-4.—Comparative Characteristics of Copper and Aluminum
Copper has a higher conductivity than aluminum. It is more ductile (can be drawn out). Copper has
relatively high tensile strength (the greatest stress a substance can bear along its length without tearing
apart). It can also be easily soldered. However, copper is more expensive and heavier than aluminum.
Although aluminum has only about 60 percent of the conductivity of copper, its lightness makes long spans
possible. Its relatively large diameter for a given conductivity reduces corona. Corona is the discharge of
electricity from the wire when it has a high potential. The discharge is greater when smaller diameter wire is
used than when larger diameter wire is used. However, the relatively large size of aluminum for a given
conductance does not permit the economical use of an insulation covering.
Q14. State two advantages of
using aluminum wire for carrying electricity over long distances.
Q15. State four advantages of copper
over aluminum as a conductor.
The resistance of pure metals, such as silver, copper, and
aluminum, increases as the temperature increases. However, the resistance of some alloys, such as constantan and
manganin, changes very little as the temperature changes. Measuring instruments use these alloys because the
resistance of the circuits must remain constant to get accurate measurements.
In table 1-1, the
resistance of a circular-mil-foot of wire (the specific resistance) is given at a specific temperature, 20º C in
this case. It is necessary to establish a standard temperature. As we stated earlier, the resistance of pure
metals increases with an increase in temperature. Therefore, a true basis of comparison cannot be made unless the
resistances of all the substances being compared are measured at the same temperature. The amount of increase in
the resistance of a 1-ohm sample of the conductor per degree rise in temperature above 0º C is called the
temperature coefficient of resistance. For copper, the value is approximately 0.00427 ohm.
A length of
copper wire having a resistance of 50 ohms at an initial temperature of 0º C will have an increase in resistance
of 50 x 0.00427, or 0.214 ohms. This applies to the entire length of wire and for each degree of temperature rise
above 0º C. A 20º C increase in resistance is approximately 20 ´ 0.214, or
4.28 ohms. The total resistance at 20º C is 50 + 4.28, or 54.28 ohms.
Q16. Define the temperature
coefficient of resistance.
Q17. What happens to the resistance of copper when it is heated?
To be useful and safe, electric current must be forced to flow only where it is needed. It must be
"channeled" from the power source to a useful load. In general, current-carrying conductors must not be allowed to
come in contact with one another, their supporting hardware, or personnel working near them.
To accomplish this, conductors are coated or wrapped with various materials. These materials have such a high
resistance that they are, for all practical purposes, nonconductors. Nonconductors are generally referred to as
"insulators" or "insulating material."
Only the necessary minimum amount of insulation is applied to any
particular type of conductor designed to do a particular job. This is done because of several factors. The
expense, stiffening effect, and a variety of physical and electrical conditions under which the conductors are
operated must be taken into account. Therefore, there are a variety of insulated conductors available to meet the
requirements of any job.
Two fundamental properties of insulating materials (that is, rubber, glass,
asbestos, or plastic) are insulation resistance and dielectric strength. These are two entirely different and
Insulation resistance is the resistance to current leakage through
the insulation materials. Insulation resistance can be measured with a megger without damaging the insulation.
Information so obtained is a useful guide in appraising the general condition of insulation. Clean, dry insulation
having cracks or other faults may show a high value of insulation resistance but would not be suitable for use.
Dielectric strength is the ability of an insulator to withstand
potential difference. It is usually expressed in terms of the voltage at which the insulation fails because of the
electrostatic stress. Maximum dielectric strength values can be measured only by raising the voltage of a TEST
SAMPLE until the insulation breaks down.
Q18. Compare the resistance of a conductor to that of an
Q19. State two fundamental properties of insulating materials.
Q20. Define insulation resistance.
Q21. Define dielectric strength.
Q22. How is the dielectric strength of an insulator determined?
TYPES OF INSULATION
The insulating materials discussed in the next paragraphs are commonly used in Navy electrical and electronic
One of the most common types of insulation is rubber. The voltage that
may be applied to a rubber- covered conductor is dependent on the thickness and the quality of the rubber
covering. Other factors being equal, the thicker the insulation, the higher may be the applied voltage. Rubber
insulation is normally used for low- or medium-range voltage. Figure 1-7 shows two types of rubber-covered wire.
One is a two-conductor cable in which each stranded conductor is covered with rubber insulation; the other is a
single, solid conductor. In each case, the rubber serves the same purpose: to confine the current to its
Figure 1-7.—Rubber insulation.
Referring to the enlarged cross-sectional view in figure 1-7, note that a thin coating of tin separates
the copper conductor from the rubber insulation. If the thin coating of tin were not used, a chemical action would
take place and the rubber would become soft and gummy where it makes contact with the copper. When small, solid,
or stranded conductors are used, a winding of cotton threads is applied between the conductors and the rubber
CODE-GRADED RUBBER.—Code-graded rubber is the standard that the National Electrical Code
(NEC) has adopted as the minimum requirements for rubber insulation as specified by Underwriters' Laboratories. In
this code system, the letter R indicates the use of a rubber insulator. Type R signifies that the wire is rubber
The NEC codes Type RH and Type RHH signify a rubber heat-resistant compound. Type RW signifies a
rubber moisture-resistant compound. A Type RHW signifies a rubber heat- and moisture- resistant compound. Type RHW
is approved for use in wet or dry locations at a maximum conductor temperature of 75º C. Neoprene, a low-voltage
compound, is the one exception to Type RHW. Although not a rubber compound, neoprene meets the requirements of
Underwriters' Laboratories and was designated Type RHW.
LATEX RUBBER.—Latex rubber is a
high-grade compound consisting of 90 percent unmilled grainless rubber. There are two designations for this type
of insulation: Type RUH and Type RUW. Type RUH (rubber unmilled heat-resistant) is used in dry locations when the
conductor temperature does not exceed 75º C. Type RUW (rubber unmilled moisture-resistant) is used in wet
locations when the conductor does not exceed 60º C.
SILICONE.—Silicone is a rubber
compound that does not carry the "R" designator for many of its applications. An example of this is Type SA
(silicone-asbestos). In Type SA, the insulator around the conductor is silicone rubber, but the outer covering
must consist of heavy glass, asbestos-glass, or asbestos braiding treated with a heat, flame, and
Q23. What is the purpose of coating a copper conductor with tin when
rubber insulation is used?
Plastic is one of the more commonly used types of insulating
material for electrical conductors. It has good insulating, flexibility, and moisture-resistant qualities.
Although there are many types of plastic insulating materials, thermoplastic is one of the most common. With the
use of thermoplastic, the conductor temperature can be higher than with some other types of insulating materials
without damage to the insulating quality of the material. Plastic insulation is normally used for low- or
The designators used with thermoplastics are much like those used with rubber
insulators. The following letters are used when dealing with NEC type designators for thermoplastics:
N Outer nylon jacket
For example, a NEC designator of Type THWN would indicate thermoplastic heat- and moisture- resistant
with an outer nylon jacket.
Varnished cambric insulation can
withstand much higher temperatures than rubber insulation. Varnished cambric is cotton cloth that has been coated
with an insulating varnish. Figure 1-8 shows a cable covered with varnished cambric insulation. The varnished
cambric is in tape form and is wound around the conductor in layers. An oily compound is applied between each
layer of the tape to prevent water from seeping through the insulation. It also acts as a lubricant between the
layers of tape, so they will slide over each other when the cable is bent.
Figure 1-8.—Varnished cambric insulation.
Cambric insulation is used on extremely high-voltage conductors used in substations and powerhouses. It
is also used in other locations subjected to high temperatures. In addition, it is used on the coils and leads of
high-voltage generators. Transformer leads also use this insulation because it is unaffected by oils or grease and
has high dielectric strength. Varnished cambric and paper insulation for cables are the two types of insulating
materials most widely used at voltages above 15,000 volts. Such cable is always lead covered to keep out moisture.
Extruded polytetrafluoroethylene is a
high-temperature insulation used extensively in aircraft and equipment installations. It will not burn, but will
vaporize when subjected to intense heat. Conductors for high temperatures use a nickel coating rather than tin or
silver to prevent oxidation. Nickel-coated wire is more difficult to solder, but makes satisfactory connections
with proper soldering techniques.
Avoid breathing the vapors from extruded polytetrafluoroethylene insulation when it is
heated. Symptoms of overexposure are dizziness or headaches. These symptoms disappear upon exposure to fresh air.
Q24. What safety precaution should you take when working with extruded polytetrafluoroethylene
Fluorinated Ethylene Propylene (FEP)
FEP has properties similar
to extruded polytetrafluoroethylene, but will melt at soldering temperatures. It is rated at 200º C and is,
therefore, considered a high-temperature insulation. There are no known toxic vapors from FEP. Common-sense
practice, however, requires that you provide adequate ventilation during any soldering operation.
Asbestos insulation was used extensively in the past for high-temperature insulation. Today, it is seldom used by
the Navy. Many naval ships and aircraft, however, still contain asbestos-insulated wiring. Aboard ship, this is
particularly true in galley and laundry equipment. The reason for discontinuing the use of asbestos as an
insulator is that breathing asbestos fibers can produce severe lung damage. It can render you disabled or cause
fatal fibrosis of the lungs. Asbestos is also a factor in the development of cancer in the gastrointestinal tract.
Safety precautions concerning asbestos will be covered in more detail at the end of chapter 3.
Avoid inhalation of asbestos fibers. Asbestos fibers have been found to cause severe
lung damage (asbestosis) and cancer of the gastrointestinal tract. Follow Navy safety precautions when working
with all asbestos products.
One type of asbestos-covered wire is shown in figure 1-9. It consists of stranded copper conductors
covered with felted asbestos. The wire is, in turn, covered with asbestos braid. This type of wire is used in
motion-picture projectors, arc lamps, spotlights, heating element leads, and so forth.
Figure 1-9.—Asbestos Insulation.
Another type of asbestos-covered cable is shown in figure 1-10. It is combination of asbestos and
varnished cambric. This type of insulation serves as leads for motors and transformers that sometimes must operate
in hot, damp locations. The varnished cambric covers the inner layer of felted asbestos. This prevents moisture
from reaching the innermost layer of asbestos. Asbestos loses its insulating properties when it becomes wet. It
will, in fact, become a conductor. Varnished cambric prevents this from happening because it resists moisture.
Although this insulation will withstand some moisture, it should not be used on conductors that may at times be
partially immersed in water. Under those circumstances, the insulation must be protected with an outer lead
Figure 1-10.—Asbestos and varnished cambric insulation.
The NEC has designators for eight types of asbestos wire. The designators and a description of each
are listed below.
Type A Nonimpregnated asbestos without an asbestos braid
Nonimpregnated asbestos with an outer asbestos braid or glass
Type AI Impregnated asbestos without an
Type AIA Impregnated asbestos with an outer asbestos braid or glass
Asbestos, varnish-cambric insulation with an outer asbestos braid or glass
Type AVL Asbestos,
varnish-cambric insulation with an outer asbestos braid covered with a lead sheath
Type AVB Asbestos,
varnish-cambric insulation with an outer flame-retardant cotton braid
Type SA Silicone rubber
insulated with outer heavy glass, asbestos-glass, or asbestos braid
Q25. State the reasons that
the Navy is getting away from the use of asbestos insulation.
Q26. State what happens to the insulating
characteristics of asbestos when it gets wet.
Paper has little
insulation value alone. However, when impregnated with a high grade of mineral oil, it serves as a satisfactory
insulation for extremely high-voltage cables. The oil has a high dielectric strength, and tends to prevent
breakdown of the paper insulation. The paper must be thoroughly saturated with the oil. The thin paper tape is
wrapped in many layers around the conductors, and then soaked with oil.
The three-conductor cable shown
in figure 1-11 consists of paper insulation on each conductor. It has a spirally wrapped nonmagnetic metallic tape
over the insulation. The space between conductors is filled with a suitable spacer to round out the cable. Another
nonmagnetic metal tape is used to secure the entire
cable. Over this, a lead sheath is applied. This type of cable is used on voltages from 10,000 volts
Figure 1-11.—Paper-insulated power cables.
Q27. What are the most common insulators used for extremely high voltages?
Silk and Cotton
In certain types of circuits (for example, communications circuits), a
large number of conductors are needed, perhaps as many as several hundred. Figure 1-12 shows a cable containing
many conductors. Each is insulated from the others by silk and cotton thread. Because the insulation in this type
of cable is not subjected to high voltage, the use of thin layers of silk and cotton is satisfactory.
Figure 1-12.—Silk and cotton Insulation.
Silk and cotton insulation keeps the size of the cable small enough to be handled easily. The silk and
cotton threads are wrapped around the individual conductors in reverse directions. The covering is then
impregnated with a special wax compound.
The wire used on the coils of
meters, relays, small transformers, motor windings, and so forth, is called magnet wire. This wire is insulated
with an enamel coating. The enamel is a synthetic compound of cellulose acetate (wood pulp and magnesium). In the
manufacturing process, the bare wire is passed through a solution of hot enamel and then cooled. This process is
repeated until the wire acquires from 6 to 10 coatings. Thickness for thickness, enamel has higher dielectric
strength than rubber. It is not
practical for large wires because of the expense and because the insulation is readily fractured when
large wires are bent.
Figure 1-13 shows an enamel-coated wire. Enamel is the thinnest insulating coating
that can be applied to wires. Hence, enamel-insulated magnet wire makes smaller coils. Enameled wire is sometimes
covered with one or more layers of cotton to protect the enamel from nicks, cuts, or abrasions.
Figure 1-13.—Enamel Insulation.
Q28. What is the common name for enamel-insulated wire?
Mineral-insulated (MI) cable was developed to meet the needs of a noncombustible, high heat- resistant, and
water-resistant cable. MI cable has from one to seven electrical conductors. These conductors are insulated in a
highly compressed mineral, normally magnesium oxide, and sealed in a liquidtight, gastight metallic tube, normally
made of seamless copper (figure 1-14).
Figure 1-14.—Two-conductor mineral-insulated (MI) cable.
Wires and cables are generally subject to abuse. The type
and amount of abuse depends on how and where they are installed and the manner in which they are used. Cables
buried directly in the ground must resist moisture, chemical action, and abrasion. Wires installed in buildings
must be protected against mechanical injury and overloading. Wires strung on crossarms on poles must be kept far
enough apart so that the wires do not touch. Snow, ice, and strong winds make it necessary to use conductors
having high tensile strength and substantial frame structures.
Introduction to Matter, Energy, and Direct Current,
to Alternating Current and Transformers, Introduction to Circuit Protection,
Control, and Measurement
, Introduction to Electrical Conductors, Wiring Techniques,
and Schematic Reading
, Introduction to Generators and Motors
Introduction to Electronic Emission, Tubes, and Power Supplies,
Introduction to Solid-State Devices and Power Supplies
Introduction to Amplifiers, Introduction to
Wave-Generation and Wave-Shaping Circuits
, Introduction to Wave Propagation, Transmission
Lines, and Antennas
, Microwave Principles,
, Introduction to Number Systems and Logic Circuits, Introduction
to Microelectronics, Principles of Synchros, Servos, and Gyros
Introduction to Test Equipment
, Radar Principles,
The Technician's Handbook,
Master Glossary, Test Methods and Practices,
Introduction to Digital Computers,
Magnetic Recording, Introduction to Fiber Optics